UCS 6000 universal control panel in cabinet equipped from one to eight MGL-60 modules with option up to 4 MPW-60 modules. Dimensions of cabinet 753x630x190 mm.
The UCS 6000 universal control panel is designed for actuation of fire protection devices, used for mechanical or gravitation smoke ventilation (fire dampers, smoke exhaust dampers etc.) and enables the following:
The UCS 6000 control panel can operate as an independent or multi -zone universal smoke exhaust controller or as an addressable device, which is installed in addressable loops of the POLON 4000 and POLON 6000 system control panels.
Equipment of control panel:
The control panel can be equipped with (*maximum number of modules in the control panel depends on the version of cabinet):
MGS-60 module (x1):
MGL-60 module (x8):
MPW-60 module (x4):
MPD-60 module (x1):
MKA-60 module (x1):
MZU-60 module (x4):
The primary purpose of the UCS 6000 control panel, in addition to fire hazard detection, is to control and power supply fire protection devices such as various types of fire/smoke dampers, fire protection windows (equipped with electricservomotors), and fire zone separators (electromagnets), etc.
For the purpose of control and supply of the mentioned devices, there is a dedicated output of a main relay installed in the MGL-60 module.
The output of the main relay is universal and can be programmed for three operation modes – with appropriate time parameters.
Additionally, continuity of power supply and monitoring the status of ending switches can be programmed for all fire protection devices controlled and supplied by the main output.
Due to a variety of power supply and control of servomotors and electric fire prevention device drives, in addition to output operation modes, control of two-direction servomotors, double wire or triple wires were implemented.
For detection of a fire, there is a detector line dedicated with the 40 model range conventional detectors. This line has the ability to program the alarm variant with preliminary reset (60 seconds) to eliminate false alarm activation.
Activation of fire protection devices in the smoke exhaust control unit is possible thanks to the following:
In an event of receiving an initiation alarm signal, smoke exhaust procedure is commenced. It is done in accordance to a pre-determined smoke exhaust procedure for a given facility. At this time ventilation push buttons are blocked, signals from rain and/or wind are ignored.
In quiescent mode, it is possible to perform day ventilation – using windows or ventilation dampers.
UCS 6000 control panel modules are equipped with a set of universal inputs and outputs for connection of external smoke exhaust installations.
Special computer application - UCS (UCS Konfigurator) is used for programming the UCS 6000 control panels. The control panel is connected to a computer using USB interface.
Design and basic versions of UCS 6000:
The UCS 6000 control panel is off ered in three cuboid shape cabinet versions:
All cabinets are made in a form of cuboid steel casings, where the smaller and the middle one is dedicated for wall mounting installation and the larger one – because of its heavy weight – is dedicated for installation as a standing version (on the floor) and fastened to the wall (for more stability).
All necessary modules required for proper operation of the control panel are placed inside the cabinets (including power supply modules and reserve batteries).
Basic versions of UCS 6000 4 A up to 32 A (cabinet dimens.: 753x630x190 mm):
Besides the above-mentioned versions, there are dozen more versions available (in different configurations) from 4 A to 64 A.
A set of control panel covers the following functional modules:
16VDC - 30VDC
|Detection line load according to selected operating mode|
|Operating temperature range|
-10°C to 55°C